SNMP MIB for PDU outelet on/off
You can use the OID .22.214.171.124.4.1.174126.96.36.199.1.13 to control the PDU.
The argument 1 means to turn on the outlet
The argument 0 means to turn off the outlet
The argument 5 means unchanging outlet status
Get OID .188.8.131.52.4.1.174184.108.40.206.1.13
If PDU respond 1,1,1,1,1,1,1,1 means outlet A~H are power on
If PDU respond 0,1,1,1,1,1,1,1 means outletA is power off, the other outlets are power on
Set OID .220.127.116.11.4.1.17418.104.22.168.1.13,
Send 1,1,1,1,0,0,0,0 means to turn on outletA~D, turn off outletE~H
Send 1,5,5,5,5,5,5,5 means to only turn on outletA, the other outlets have not action.
Get OID .22.214.171.124.4.1.174126.96.36.199.2.13
If PDU respond 0,0,0,0,0,0,0,1 means outlet I~O outlets are power off, only Outlet P is power on.
If PDU respond 1,0,0,1,1,1,1,1 means outlet J and K is power off, the other outlets are power on
Set OID .188.8.131.52.4.1.174184.108.40.206.2.13,
Send 1,1,1,1,0,0,0,0 means to turn on outlet I~L, turn off outlet M~P
Send 5,0,5,5,5,5,5,5 means to only turn off outlet J , the other outlets have not action.
The argument 5 does not apply all of PDU. Please check our sales personnel to get information.